AC Power & Comfort came to a Delray Beach health facility to repair a chiller for the MRI machine.
- Replaced the compressor which was shorted to ground
- Replaced liquid line dryer
- After putting the compressor we verified that the condenser fan motor was not operational, which we also replaced
- Performed a quick sanitization of the condenser coil
- Confirmed temperature was reached to 50F and noticed pressure decreased as expected